Boiler Blog | Nationwide Boiler Inc.
Boiler Basics 101: Economizers for Increased Efficiency
The price of fuel is constantly fluctuating and with it comes creative ways to be more economical. Finding methods to be more energy efficient is never a waste of time. In the boiler room, efficiency improvements can be found by many sources, however, a common option for energy savings includes the use of an economizer. What is an economizer? The economizer is a fabricated assembly of finned tubing that captures waste heat extracted from the boiler’s stack flue gases; the exhaust that leaves the boiler stack (or “flue”).
It’s all about the principle of Heat Transfer. While low temperature water, or feedwater, enters a boiler system, high temperature flue gas exits. An economizer captures heat from the flue gas that would typically go to waste, and utilizes it to preheat the feedwater. By doing this, an economizer is able to increase thermal efficiency by decreasing the energy required to heat the water to steam. This will typically result in a reduction of 1% in fuel cost per 10 degree rise in feedwater temperature. Overall, an economizer can be a major cost savings for boiler owners and will easily provide a quick return on investment.
The economizers’ simple technology and static parts provide longevity and low maintenance, and they are available in multiple designs and configurations. Conventional economizers are cylindrical or rectangular and come in a range of sizes for both firetube and watertube boilers. Rectangular designs are more commonly used for larger industrial watertube boilers, and can be configured for vertical or horizontal gas flows, finned or bare tube design, and other additional options if needed. A condensing economizer can improve waste heat recovery even further by cooling the flue gas below its dew point, reclaiming both sensible heat from the flue gas and latent heat by condensing the flue gas water vapor.
|BOILER EFFICIENCY COMPARISON
|Combustion Efficiency at
4% Excess Oxygen
|78% to 83%
|350F to 355F
|Boiler with Standard Economizer
|84% to 86%
|250F to 300F
|Boiler with Condensing Economizer
|92% to 95%
|80F to 150F
When determining whether an economizer is ideal for your boiler equipment, the location of the economizer into stack is important. To ensure the most thermal recovery during the process, you need to make sure the economizer is installed as close to the furnace breach as possible. This will help avoid thermal loss and cooling.
At Nationwide Boiler, we offer our EconoStak economizer as an optional addition (or a standard addition in some cases) on our fleet of watertube rental boilers. The EconoStak consists of the economizer as well as all of the associated piping and structural supports required for very efficient and safe operation. In addition, we are a West Coast representative for E-Tech Heat Recovery Systems, a leading provider of economizers for new, replacement, and retrofit applications.
Contact Nationwide Boiler today to see if an economizer is the right option for you, and be sure to check out our previous Boiler Basics 101 blogs. We review various topics each month, so stay tuned for the next edition!