Boiler Blog | Nationwide Boiler Inc.
Boiler Basics 101: Blowdown
Routine maintenance on your boiler is a critical component for proper and efficient boiler operation. One of the main factors to improper maintenance that can also lead to boiler failure is not understanding the concept of blowdown. In this month’s Boiler Basics 101, we will be going over what blowdown is and how it will help improve your boiler’s health.
When boiler water turns to steam, solids from the water are left behind. The blowdown process involves partially draining the boiler to remove the sludge those solids create. If these are not removed, boiler performance will be reduced and ultimately, it can lead to boiler failure.
Industrial boilers have three types of blowdown procedures:
- Low Water Cutoff
This blowdown procedure should take place after every shift. The water column must be kept clean to ensure the water level in the gauge glass accurately represents the water level in the boiler. Regular checks on the boiler verifies that the low water cutoff is operating correctly and cleans it out.
- Bottom Blowdown
Bottom blowdown is done by manually opening a set of two valves that drains water out of the bottom of the boiler. The purpose of the bottom blowdown activity is to clean out solids that accumulate at the bottom of a firetube boiler or in the mud drum of a watertube boiler. Solids are pushed through a blowdown separator designed to take water from the boiler during blowdown and reduce it to atmospheric pressure for disposal. During this process, steam is rapidly separated from blowdown water and vented out the top of the blowdown separator. From there, the cooled blowdown solids can be safely removed from the boiler.
- Continuous Blowdown
The purpose of the continuous blowdown is to help control the water quality in the boiler; the more impurities and the more chemical treatment required, the greater the amount of blowdown required. It is a procedure facilitated by a pipe entering the upper section of the boiler, typically located in the steam drum of a watertube boiler or the upper steaming portion of a firetube boiler.
The continuous blowdown process is generally automated and does not require much manual interaction, like with bottom blowdown. When operating continuous blowdown, adjust the valve to maintain the recommended boiler water dissolved solids level. This helps control the dissolved solids in boilers that are operated at a steady load.
It is important to consider proper blowdown procedures to keep the water piping clean and the boiler in working condition.
Be sure to check out our previous Boiler Basics 101 blogs and stay tuned for the next edition!